These energy saving timers use n
Upgrading to an electronic time switch has never been
easier than now with the new ET1700 Series. Features include; Automatic Daylight
Saving Time adjustment, multi-volt operation from 120 to 277 VAC, and
to-the-minute programming for accurate load control and reduced energy costs. Up
to 28 set points or events (14 ON/14 OFF per channel) can be distributed
throughout the days of the week. The program can be overridden at any time. Two
industrial grade "AAA" alkaline batteries provide 3 years minimum program and
- Model #: ET1725C²
- Circuits: 2
- Switch: STST
- Clock Voltage: 120/208/240/277
- Amp Rating: 30
- HP Rating: 1HP/ 2HP
- Enclosure: NEMA 1
Options: Standard: NEMA 1 Grey Painted Drawn Steel; 'R' Option: NEMA 3R Grey
Paited Drawn Steel; 'PD82' Option: NEMA 3R Grey High-Impact UV Resistant
Polycarbonate Plastic with Clear Cover
electronic mechanism snaps into the standard Intermatic time switch case,
replacing mechanical mechanisms, if desired.
Combination 1/2"-3/4" nominal knockouts, one on back and each side of case
and two on bottom.
Voltages and Cycles: ALL models 50 or 60 Hz.
Rating: 30 Amp Inductive/Resistive, 24/ 120/ 240/ 277 VAC 60 Hz; 20 Amp
Resistive, 28 VDC; 1 HP 120 AVC 60 Hz; 2 HP 240 VAC 60 Hz; 5 Amp Tungsten, 120/
240/ VAC 60 Hz; 20 Amp Ballast, 120-277VAC 60 Hz. ET100C same ratings for 120
Volt loads only. ET1115 models normally closed contact ratings: 10A
Resistive/General purpose, 12-277VAC; 10A Resistive/General purpose, 28 VDC; 3A
Ballast, 120-277VAC; 1/4 HP, 120 VAC; 1/2 HP, 240 VAC; 30 LRA; 12 FLA; 275 VA
pilot duty, 120-240 VAC
Feature: 2 Circuit models feature 2-Second pulse option for contactor and
bell ringing applications
Automatic Adjustment for Daylight Saving Time (DST)
Field replaceable "AAA" batteries maintain program and accurate time keeping
for 3 years minimum. Up front replacement does not require removal of mechanism.
Terminals: #18 to #10 AWG wire
ON/OFF Times: 1 minute
ON/OFF Times: 6 days 23 hours 59 minutes
ET8725 Models feature contacts that can be field configured to act as two
independently operated SPST, one simultaneous operated DPST, or independently
pulsed SPST for contactor and bell ringing applications.